IESNA:LM-63-2002
[TEST] P93847
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21038)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6840 6LN0W
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH GLOSS WHITE TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]1019
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]1019
TILT=NONE
1 1019 1 37 1 1 1 -0.541667 -0.541667 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
997.1 980.7 935.6 873.3 801.9 733.1 680.6 642 608.5 575.6
542.8 510.9 474.8 424 359.1 290.3 227.9 178.8 143.5 119.7
104.1 92.6 82 72.1 63.1 55.7 48.3 41 35.2 29.5
23.8 18.8 14.8 9.9 6.5 2.5 0
