IESNA:LM-63-2002
[TEST] P94601
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21524)
[TESTLAB]Innovations Center P2
[ISSUEDATE]8/22/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_620DLUT ERW6840H20 6LW0WB
[LUMINAIRE]PORTFOLIO 6 INCH 60 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]WIDE DISTRIBUTION WITH WHITE BAFFEL TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]-1
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]-1
TILT=NONE
1 -1 1 37 1 1 1 -0.458333 -0.458333 0
1 1 38.6
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1065.1 1060.2 1052.4 1051.4 1049.5 1038.7 1025.1 1011.4 989.9 959.5
921.5 877.5 824.7 759.3 681.1 596.1 510 429.9 361.6 305.8
261.8 227.7 201.3 178.8 159.3 139.7 122.1 105.5 89.9 75.2
61.6 48.9 36.2 24.4 13.7 4.9 0
