IESNA:LM-63-2002
[TEST] P93827
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21103)
[TESTLAB]Innovations Center P2
[ISSUEDATE]2/11/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6840 6LM0WB
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH WHITE BAFFEL TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]881
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]881
TILT=NONE
1 881 1 37 1 1 1 -0.541667 -0.541667 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
606.8 603.5 598.6 596.9 594.4 587.1 576.5 567.4 551.8 528.9
497.8 456.7 402.6 337.8 272.2 216.5 175.5 146.8 128 113.2
100.8 90.2 82 73.8 66.4 58.2 51.7 45.1 38.6 32.8
27 22.1 17.3 12.3 8.2 4.1 0
