IESNA:LM-63-2002
[TEST] P93794
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20833)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6835 6LM0WMH
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH WARM HAZE TRIM
[LAMP](1) HIGH LUMEN LED 3500K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]902
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]902
TILT=NONE
1 902 1 37 1 1 1 -0.489583 -0.489583 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1009.2 1000.3 979.8 959.4 931.7 892.4 848.3 803.4 754.5 702.2
642.6 573.2 490.8 397.6 302.9 219.6 154.3 107.7 75.1 53.1
37.6 26.9 20.4 15.5 11.4 8.2 6.5 4.9 3.3 2.5
1.7 0.8 0.8 0.8 0 0 0
