IESNA:LM-63-2002
[TEST] P93784
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20837)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6835 6LM0GP
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH GRAPHITE TRIM
[LAMP](1) HIGH LUMEN LED 3500K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]642
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]642
TILT=NONE
1 642 1 37 1 1 1 -0.489583 -0.489583 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
828.8 824.6 815.7 805.9 785.5 749.5 704.7 656.5 606.7 552.8
495.6 431.2 357.7 275.2 192.7 123.3 71.8 39.2 20.4 9.8
4.9 2.5 1.7 1.7 0.8 0.8 0.8 0 0 0
0 0 0 0 0 0 0
