IESNA:LM-63-2002
[TEST] P93909
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20835)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_615D010 ERM6835 6LM0WHH
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH WHEAT HAZE TRIM
[LAMP](1) HIGH LUMEN LED 3500K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]1128
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]1128
TILT=NONE
1 1128 1 37 1 1 1 -0.489583 -0.489583 0
1 1 24.4
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1248.4 1237.7 1210.8 1182.9 1147.4 1099 1045.2 991.4 933.3 871
800 715.1 614 498.9 381.8 277.4 197.9 138.7 98.9 69.9
50.6 35.5 26.8 20.5 15.1 11.9 8.6 6.5 4.3 3.2
2.2 1.1 1.1 1.1 0 0 0
