IESNA:LM-63-2002
[TEST] P94169
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21029)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_615DLUT ERN6840 6LN0WH
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH WHEAT TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]1206
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]1206
TILT=NONE
1 1206 1 37 1 1 1 -0.458333 -0.458333 0
1 1 29.5
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
2713.7 2646.9 2453.2 2187.4 1894.2 1610.4 1372.2 1175.2 1004.8 853.3
726.4 626.8 540 447.9 346.2 244.6 159.8 95.3 52.9 27.6
13.7 4.2 2.1 2.1 2.1 1.1 0 0 0 0
0 0 0 0 0 0 0
