IESNA:LM-63-2002
[TEST] P94097
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20842)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_615DLUT ERM6840 6LM0CCH
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH CHOCOLATE HAZE TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]683
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]683
TILT=NONE
1 683 1 37 1 1 1 -0.489583 -0.489583 0
1 1 29.5
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
865.1 856.6 837.5 815.3 786.7 747.5 706.2 667 627.9 584.5
533.7 472.2 396 307.1 218.1 140.8 84.7 47.6 25.5 12.7
6.3 3.2 2.1 2.1 1.1 1.1 1.1 0 0 0
0 0 0 0 0 0 0
