IESNA:LM-63-2002
[TEST] P93584
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21103)
[TESTLAB]Innovations Center P2
[ISSUEDATE]2/11/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610D120 ERM6830 6LM0WB
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH WHITE BAFFEL TRIM
[LAMP](1) HIGH LUMEN LED 3000K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]637
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]637
TILT=NONE
1 637 1 37 1 1 1 -0.541667 -0.541667 0
1 1 14.6
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
438.8 436.4 432.8 431.7 429.9 424.6 416.9 410.3 399 382.5
359.9 330.2 291.1 244.3 196.8 156.5 126.9 106.1 92.5 81.8
72.9 65.2 59.3 53.3 48 42.1 37.4 32.6 27.9 23.8
19.6 16 12.4 8.9 5.9 3 0
