IESNA:LM-63-2002
[TEST] P93736
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21034)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6827 6LN0K
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH COGNAC TRIM
[LAMP](1) HIGH LUMEN LED 2700K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]643
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]643
TILT=NONE
1 643 1 37 1 1 1 -0.458333 -0.458333 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1262.6 1234.9 1152.9 1038.9 909.6 783.2 677.5 593.5 519.8 455.8
402.4 359.2 319 271 214.7 155 102.1 60.5 32 15.3
6.2 2.1 0.7 0.7 0.7 0.7 0.7 0 0 0
0 0 0 0 0 0 0
