IESNA:LM-63-2002
[TEST] P93410
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20836)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610D010 ERM6827 6LM0G
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH GOLD TRIM
[LAMP](1) HIGH LUMEN LED 2700K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]791
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]791
TILT=NONE
1 791 1 37 1 1 1 -0.489583 -0.489583 0
1 1 17.5
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
974 976.8 987.9 1004.5 1002.3 965.6 900.6 821.7 737.2 653.5
573.2 495 414 323.3 238.1 151.6 90.7 54.6 33.2 20.7
13.2 7.6 5.5 4.1 3.4 2.8 2.1 1.4 1.4 0.7
0.7 0.7 0 0 0 0 0
