IESNA:LM-63-2002
[TEST] P94472
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21529)
[TESTLAB]Innovations Center P2
[ISSUEDATE]8/22/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_620DLUT ERN6827H20 6LN0CCH
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH CHOCOLATE HAZE TRIM
[LAMP](1) HIGH LUMEN LED 2700K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]-1
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]-1
TILT=NONE
1 -1 1 37 1 1 1 -0.458333 -0.458333 0
1 1 38.6
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1235.7 1210.9 1140.7 1053.8 962.8 874.3 800.9 743.5 692.4 644.5
598.3 556.8 508.9 441.1 346.2 236.9 140.4 73.4 33.5 13.5
4.8 2.4 0.8 0.8 0.8 0.8 0 0 0 0
0 0 0 0 0 0 0
