IESNA:LM-63-2002
[TEST] P94289
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21534)
[TESTLAB]Innovations Center P2
[ISSUEDATE]8/22/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_620D010 ERN6835H20 6LN0K
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH COGNAC TRIM
[LAMP](1) HIGH LUMEN LED 3500K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]-1
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]-1
TILT=NONE
1 -1 1 37 1 1 1 -0.458333 -0.458333 0
1 1 34
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
3244.5 3120.4 2775.3 2370.2 1997.9 1678.2 1430 1240 1080.2 945.8
835.9 750.3 671.3 581 466.3 332.8 209.7 118.4 61.1 29.1
14.1 3.7 2.8 1.9 1.9 1.9 1 1 1 1
1 1 1 1 1 0 0
