IESNA:LM-63-2002
[TEST] P93997
[TESTLAB]Innovations Center P2
[ISSUEDATE]06/29/10
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LD615D010-ERW6830-6LW1H
[LUMCAT]LC_615D010-ERW6830-6LW0H
[MORE]DOWNLIGHT WITH HAZE TRIM, 1 PERCENT CURVED LENS, AND DRIVER
[MORE]#1 ( MODULE NUMBER AS-196,TRIM NUMBER AS-123, AND DRIVER
[MORE]NUMBER AS-166) ---ABSOLUTEPHOTOMETRY IS BASED ON CALIBRATION
[MORE]FACTORS CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET---
[OTHER]INPUT WATTS:24.323., AMPS:.2072, VOLTS:120.11, HOURS OPERATED
[MORE]PRIOR TO TESTING: 16 HRS, STABILITY: 30 MIN, TOTAL OP TIME:
[MORE]17 HRS AMB TEMP:25.2 DEG C
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]1242
[_TESTPROCEDURE]IESNA LM 79-08
[_ABSOLUTELUMENS]1242
TILT=NONE
1 1242 1 37 1 1 1 -0.5 -0.5 0
1 1 24.3
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
825.9 821.9 815.1 811.2 806.3 794.5 780.8 768.1 751.4 726.9
696.5 660.3 618.2 567.2 508.4 444.8 380.1 318.4 260.6 207.7
161.6 122.5 91.1 65.6 46 29.4 16.7 11.8 7.8 4.9
3.9 2 2 1 1 0 0
