IESNA:LM-63-2002
[TEST] P94385
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21524)
[TESTLAB]Innovations Center P2
[ISSUEDATE]8/22/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_620D010 ERW6840H20 6LW0WB
[LUMINAIRE]PORTFOLIO 6 INCH 60 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]WIDE DISTRIBUTION WITH WHITE BAFFEL TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]-1
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]-1
TILT=NONE
1 -1 1 37 1 1 1 -0.458333 -0.458333 0
1 1 34
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1046.6 1041.8 1034.1 1033.2 1031.3 1020.7 1007.3 993.8 972.7 942.9
905.5 862.2 810.4 746.1 669.3 585.7 501.3 422.4 355.3 300.6
257.3 223.8 197.8 175.7 156.5 137.3 120.1 103.7 88.3 73.9
60.5 48 35.5 24 13.4 4.8 0
