IESNA:LM-63-2002
[TEST] P94084
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21103)
[TESTLAB]Innovations Center P2
[ISSUEDATE]2/11/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_615DLUT ERM6835 6LM0WB
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH WHITE BAFFEL TRIM
[LAMP](1) HIGH LUMEN LED 3500K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]1132
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]1132
TILT=NONE
1 1132 1 37 1 1 1 -0.541667 -0.541667 0
1 1 29.5
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
780.1 775.9 769.7 767.6 764.4 754.9 741.1 729.6 709.5 680.1
640 587.3 517.6 434.4 350 278.4 225.6 188.7 164.4 145.5
129.7 115.9 105.5 94.9 85.4 74.8 66.4 58 49.6 42.2
34.8 28.4 22.1 15.8 10.6 5.3 0
