IESNA:LM-63-2002
[TEST] P93735
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21005)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6827 6LN0H
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH SEMI-SPECULAR CLEAR TRIM
[LAMP](1) HIGH LUMEN LED 2700K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]765
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]765
TILT=NONE
1 765 1 37 1 1 1 -0.489583 -0.489583 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
929.8 921.4 897.2 864.5 819.3 762.3 708.8 659.5 608.1 556
504.5 455.8 407.2 349.6 282.2 212.6 150.8 101.4 66.7 43.8
29.9 18.7 13.9 10.5 8.4 6.2 4.8 3.5 2.8 2.1
1.4 1.4 0.7 0.7 0 0 0
