IESNA:LM-63-2002
[TEST] P93843
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21005)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6840 6LN0H
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH SEMI-SPECULAR CLEAR TRIM
[LAMP](1) HIGH LUMEN LED 4000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]902
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]902
TILT=NONE
1 902 1 37 1 1 1 -0.489583 -0.489583 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1097.1 1087.3 1058.6 1020.1 966.8 899.5 836.4 778.2 717.5 656
595.3 537.9 480.5 412.4 332.9 250.9 177.9 119.7 78.7 51.7
35.2 22.1 16.4 12.3 9.9 7.4 5.7 4.1 3.3 2.5
1.7 1.7 0.8 0.8 0 0 0
