IESNA:LM-63-2002
[TEST] P93753
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20831)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610DLUT ERM6830 6LM0LI
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH SPECULAR CLEAR TRIM
[LAMP](1) HIGH LUMEN LED 3000K
[BALLAST]LUTRON ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]971
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]971
TILT=NONE
1 971 1 37 1 1 1 -0.489583 -0.489583 0
1 1 20.9
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1240 1236.4 1228.9 1224.3 1206.5 1160.1 1091.4 1009.2 916.6 818.7
719.4 619.3 515.4 401.9 292.8 192 115 64.2 35.8 20.1
11.9 5.2 3.7 3 2.3 2.3 1.5 1.5 0.8 0.8
0.8 0 0 0 0 0 0
