IESNA:LM-63-2002
[TEST] P93559
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P20840)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_610D120 ERM6827 6LM0KH
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]MEDIUM DISTRIBUTION WITH COGNAC HAZE TRIM
[LAMP](1) HIGH LUMEN LED 2700K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]448
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]448
TILT=NONE
1 448 1 37 1 1 1 -0.489583 -0.489583 0
1 1 14.65
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
530.6 525.7 513.6 499.8 481.5 458.4 434.1 411 387.2 361.3
331.5 296.1 252.6 201.8 150 104.8 70.1 46.3 30.4 19.8
12.7 8.3 6.1 4.4 2.8 2.2 1.7 1.1 0.6 0.6
0.6 0 0 0 0 0 0
