IESNA:LM-63-2002
[TEST] P93943
[MORE]TEST IS SCALED FROM IESNA LM-79-08 TEST DATA (P21032)
[TESTLAB]Innovations Center P2
[ISSUEDATE]1/20/2011
[MANUFAC]COOPER LIGHTING - PORTFOLIO
[LUMCAT]LC_615D010 ERN6827 6LN0GP
[LUMINAIRE]PORTFOLIO 6 INCH 50 DEGREE CUTOFF RECESSED DOWNLIGHT
[MORE]NARROW DISTRIBUTION WITH GRAPHITE TRIM
[LAMP](1) HIGH LUMEN LED 2700K
[BALLAST]ELECTRONIC DRIVER
[_MOUNTING]RECESSED
[_ABSOLUTELUMENS]689
[MORE]ABSOLUTE PHOTOMETRY IS BASED ON CALIBRATION FACTORS
[MORE]CREATED USING LAB LUMEN STANDARDS IN GONIOPHOTOMETER
[MORE]WITH TEST DISTANCE OF 28.75 FEET
[_ABSOLUTELUMENS]689
TILT=NONE
1 689 1 37 1 1 1 -0.458333 -0.458333 0
1 1 24.4
0 2.5 5 7.5 10 12.5 15 17.5 20 22.5
25 27.5 30 32.5 35 37.5 40 42.5 45 47.5
50 52.5 55 57.5 60 62.5 65 67.5 70 72.5
75 77.5 80 82.5 85 87.5 90
0
1162.3 1137.5 1067.1 969.2 859.4 756.8 673.5 608.6 553.7 505.1
461.2 422.8 381.6 327.6 258 184 118.1 66.8 32.9 13.7
3.6 0.9 0.9 0.9 0 0 0 0 0 0
0 0 0 0 0 0 0
